A fueling facility in Tanknology’s Northwest region requested a TankCam inspection of a 12,000 gallon lined, steel tank to inspect for undesirable conditions or abnormal operating conditions. The tank held regular unleaded.
The TankCam inspection found drips falling from an area at or around the STP riser and from the upper tank wall near the endcap. The inspection also found water staining and missing lining near the ATG riser. The video also showed sediment and debris on the tank bottom.
TankCam® video inspection services from Tanknology help you detect UST problems with no need for excavation or manned entry. TankCam is patent pending.